3A-GM ™ -Oil oil-water coalescing separator GM ™ -Oil oil-water coalescing separator is divided into two types: one is to remove water from oil, and the other is to remove oil from water. The common point of the two is to separate the components with a small proportion from the materials with a large proportion. Due to the density difference between water and oil, the two groups of materials through the secondary separation of the filter core are completely separated. Oil-water separator is also called oil-water separator, coalescer, separator, etc.
3A-GM ™ -Oil oil-water coalescing separator
GM ™ -Oil oil-water coalescing separator is divided into two types: one is to remove water from oil, and the other is to remove oil from water. The common feature of the two is to change the less
The materials are separated. Due to the density difference between water and oil, the two groups of materials through the secondary separation of the filter core are completely separated. Oil-water separator, also known as oil-water separator, coalescing
, Separator, etc.
Function: agglomerate small liquid droplets into large liquid droplets, and drop it into the collecting tank. Function: lipophilic and hydrophobic
Product model of coalescer
Water separation inside GM ™ -Oil-I oil
After the material enters the filter separator through the inlet, it is first collected in the tray, and then dispersed into the coalescing filter element from the inside to the outside, and the solid impurities are filtered by the filter layer, and the second step passes
The demulsification layer separates the oil and water in the emulsified state. In the third step, tiny water droplets are aggregated into large droplets by the coalescing layer and settled in the water collecting tank;
It is further separated by the water repellent action of the separation filter element, settles in the sedimentation tank, and is discharged by the drainage valve. Clean fuel is collected in the secondary tray through the separation filter, and
Use and maintenance
After the filter separator is installed, it can work continuously and reliably for a long time. Generally, it is not necessary to clean the cover, but the following points should be paid attention to when using it:
1) Deflate in time. For the filter equipped with a manual air release valve, manual air release is required for each operation, because too much gas accumulated in the housing will affect the
The filter works normally.
2) Frequent precipitation. After each refueling operation, the sediment should be placed, and it is normal for water to be in the sediment. If solid impurities are found during precipitation, the cause should be identified and
Take timely measures.
3) Persistently record the differential pressure. After each operation, the filter pressure difference and fuel throughput should be recorded in the maintenance log to determine whether the filter separator is working properly.
If a sudden drop in pressure is found, stop using it immediately and open the cover for inspection in time to find out the cause.
4) Replace the filter element.
The coalescing filter should be replaced when:
① Pressure difference reaches 0.1Mpa
② The use period exceeds six months
③ The filter element is broken (the pressure drop suddenly drops)
The separation filter should be replaced when:
① Broken filter element
② Filter element water test failed